100A transducer is used for the measurement of AC current. The system interface allows to assign transducer and to introduce the function data conversion. VT407 AC current converter can be used together with HAT-100Q1 to convert data into the format of Vutlan remote monitoring system.
Sensor is needed for measurement of temperature outdoors.
Operating temperature: −50… +105°С
Needed for light and sound alarms. Has 1.5 m in length. Connects to 12V DC, 0.25A electronic relay of Vutlan monitoring systems.
Access sensor, magnet. Needed for control of doors and windows. A dry contact input sensor.
Relay switchable contact. Can be used together with equipment, for example for switching ON/OFF air conditioners. Can control power for magnetic locks, bolt locks, solenoid electromagnets, siren, light source, heater and etc.
Can be connected to any monitoring system or device with 12V outputs.
The unit has all possibilities for rack control, PIR sensor for door control, 2 dry contacts, temperature and humidity sensors.
Operating temperature: −40… +125°С.
RH operating range: 0 to 100%.
T accuracy: ±0.4°C in –10 to 85 °C range.
RH accuracy: ± 3% RH in 0 to 80% range.
12V LED strobe flashlight for warning and alarms. Can be used with monitoring units by connecting it to 12V outputs. Cable length 2m.
Board is mounted and connected inside of VT825 DC. Adds 8 dry contacts (IN), 2 loads (latching relays with LEDs indicators) & a 12V DC power backup terminal.
Allows increasing the number of dry contacts connected to any Vutlan monitoring unit. Adds 32 dry contacts. Can be connected to any CAN port.
The number of dry contacts inside VT440 can be increased up to 64 with dry contacts module VT32.
Allows to monitor up to 32 Modbus RTU devices/meters/sensors. Max. a distance of a daisy chain is up to 1000 meters. Each metered value of a Modbus device is addressed individually using input registers and is shown by the system as virtual sensors. You can configure thresholds and icon representation for these elements.
It can be used with VT325, VT335S, VT805, VT825 monitoring systems. Installed inside the monitoring unit. Has an internal termination and by default, it is switched ON (if required can be turned off).